Conducting locations with restricted movement, Temporary installations for structures, amusement devices and booths at fairgrounds, amusement parks and circuses, and. In existing electrical installations, Type AC RCDs have been installed for many years and are effective for equipment which is resistive, capacitive or inductive and fitted with minimal electronic components. RCDs are far more sensitive than circuit-breakers. Different Types of RCD Residual Current Device is a generic term used for describing devices which incorporate residual current protection in accordance with one of the standards below: Residual Current Circuit-Breaker (RCCB) without protection against overload BS EN 61008, BS 4293, BS EN 62423. RCD does not create new documentation requirements; rather, it would only require submission of the same information currently required to be maintained. (415.1). They are designed to provide safety for three types of protection; these are:Â. Type B devices are also suitable for Type AC, Type A and Type F applications. This demonstrates how the shape of the waveform is affected on various types of circuits under load and fault conditions. It can also provide some protection against electrical fires. Industrial installations using uninterruptible power supplies (UPS) and variable speed drive (VSD) frequency inverters for the speed control of motors. This type of device protects from electric shocks in the case of residual currents that can result with electrical loads such as washing machines and pumps, for example. These are likely to be Type AC which could be ineffective due to the residual DC fault current created by types of electrical equipment. In short, an RCD protects against injury and death caused by electric shock by detecting an imbalance between the outgoing and incoming total current of a given number of circuits. Type F RCDs are designed to detect mixed frequency residual currents 10Hz< 1kHz as defined in BSEN62423. Effectively, the RCBO is the equivalent of an RCCB + MCB. The Institution of Engineering and Technology is registered as a Charity in England & Wales (no 211014) and Scotland (no SC038698), Brief introduction to the deployment of medical IT systems, IET announces new amendment to BS 7671 (IET Wiring Regulations), Setting the Standard (continued): A-Deviations. This DC current saturated the magnetic core of the RCD preventing it from tripping under the test condition. RCDs not exceeding 30 mA tripping current. flowing from the line supply conductor through the load and returning via the neutral conductor. Selection Of Types Of RCD RCD's exist in various different forms and react differently depending on the presence of DC components or different frequencies. The problem for specifiers, designers, installers, and ayone with a leagl duty over an installation is how to know which RCD is the correct one. Type A devices are also suitable for Type AC applications. The decision to fit a Type A or B will depend on the potential level of DC current and manufacturers data for the equipment would need to be consulted. What is not so commonly known is that there are different RCD types available. Where electric vehicle charging equipment is likely to create a residual DC fault current, manufacturers may provide the correct type of RCD within the charging equipment. When a fault occurs on a circuit causing a current to flow to earth, this creates an imbalance and trips the device. An RCD can detect changes in the proper flow of electric current: when a flex or cable is cut, for instance, or an electrical appliance malfunctions. Socket Outlet incorporating a Residual Current Device (SRCD) with or without overcurrent protection BS 7288.Â. The designer must consider the nature of the load in order to select the correct type of RCD. All electricians are familiar with the Residual Current Device or RCD. The Fixed RCDs â the Fixed Residual Current Devices are installed inside the consumer unit (fusebox) and can provide protection to individual or groups of circuits. Many RCDs had been installed in locations which were unsuitable due to environmental conditions. The advent of new technologies has created different challenges for the electrical designer and installer. Some equipment will have DC leakage current by the nature of design, other equipment may produce DC currents during fault conditions, dictated by the construction of the equipment. In the event of a fault the residual earth currents will also contain the non-linear currents such as pulsed DC, pure DC of high frequency AC currents. In this video we show how to set up a Megger 1741 MFT tester so we can test AC RCDâs, A Type RCDâs and B Type RCDâs. Examples include: Other examples of installations which require protection by RCDs include: It is important to select the correct Type of RCD for the equipment to be used. to be able cope with the different currents, so they continue to provide the required level of protection. A ground fault circuit interrupter (GFCI), or Residual Current Device (RCD) is a type of circuit breaker which shuts off electric power when it senses an imbalance between the outgoing and incoming current. Type F RCDs are designed to detect mixed frequency residual currents 10Hz< 1kHz as defined in BSEN62423. Assuming an AC Type RCD will suit every installation is incorrect and RCDs shall be selected according to the equipment which is likely to be used within the installation. The appropriate RCD shall be selected from the following:(i) RCD Type AC: RCD tripping on alternating sinusoidal residual current, suddenly applied or smoothlyincreasing(ii) RCD Type A: RCD tripping on alternating sinusoidal residual current and on residual pulsating direct current, suddenly applied or smoothly increasing.NOTE 1: For RCD Type A, tripping is achieved for residual pulsating direct currents superimposed on a smooth directcurrent up to 6 mA. Usually this type of consumer unit also allows for fully flexible configuration, meaning there is no restriction on the number of RCBOs used. RCD Incomer Consumer Unit. â531.3.3 Types of RCDDifferent types of RCD exist, depending on their behaviour in the presence of DC components and frequencies. Historically, two basic types of earth-leakage circuit-breaker (ELCB) were recognised by BS 7671: what we know to be a current-operated type or residual current device (RCD) and the even older voltage-operated type. Residual Current Circuit-Breaker (RCBO) with protection against overload BS EN 61009. For this reason, manufacturers provide different RCD types to be able cope with the different currents, so they continue to provide the required level of protection. If equipment contains Power Electronic Converter Systems (PECS), more commonly known as inverters or VSDs, BS 62477-1 Safety requirements for power electronic converter systems and equipment sets out the requirements and Annex H provides guidelines for RCD compatibility. Some European countries have already banned the general use of Type AC RCDs and some manufacturers have stopped making them, supplying Type A in place of Type AC. They are usually used as a sub-board to a main distribution panel. This means that faults on the DC output side, connected to the vehicle, would not be detected by an RCD on the input side of the circuit. Modern appliances are becoming increasingly more sophisticated, featuring microprocessor technology with an emphasis on energy reduction. Types of Residual Current Devices (RCD) There are three basic types of RCDs: 1. Many studies on the in-service reliability have been carried out on RCDs installed in a wide range of installations providing an insight into the effects that environmental conditions and external factors can have on the operation of an RCD. detected by the RCD. and neutral AC currents which under normal conditions should be equal and opposite in direction of flow i.e. Type B devices are designed to trip at fault currents of 3-5 times rated current (In). Each RCD type has different operating characteristics to suit particular applications - including those where DC components and varying frequencies are present. These RCD types can generate residual currents with mixed frequencies. can generate residual currents with mixed frequencies. Where necessary, equipment manufacturers should specify the RCD Type required. There are no additional requirements for the installer to check for correct operation whilst subjected to DC residual current. Type D devices are designed to trip at 10-20 times In (100-200A for a 10A device). These. Fault Protection. AC, A, B & F Type A is no more a universal solution than Type AC. A tripping current not exceeding 300 mA. For this reason, manufacturers provide different. It is constructed from coils of wire wound around a ferrite toroid core, one for each live conductor of the circuit protected. (iv) RCD Type B: RCD for which tripping is achieved as for Type F and in addition:(a) for residual sinusoidal alternating currents up to 1 kHz(b) for residual alternating currents superimposed on a smooth direct current(c) for residual pulsating direct currents superimposed on a smooth direct current(d) for residual pulsating rectified direct current which results from two or more phases(e) for residual smooth direct currents, whether suddenly applied or slowly increased, independent of polarity.NOTE 3: For RCD Type B, tripping is achieved for residual pulsating direct currents superimposed on a smooth direct current up to 0.4 times the rated residual current (IÎn) or 10 mA, whichever is the highest value.For general purposes, Type AC RCDs may be used.NOTE 4: For guidance on the correct use of RCDs for household and similar use, see PD IEC/TR 62350.NOTE 5: Some typical fault currents in circuits comprising semiconductors are given in Annex A53, Figure A53.1.â. Swimming pool installations can be at risk when equipment such as pumps are being replaced with newer equipment incorporating VSDs, without any consideration as to whether the existing Type AC RCD is still suitable for the application. e A residual-current device (RCD), residual-current circuit breaker (RCCB), or ground-fault circuit interrupter (GFCI) is a device that quickly breaks an electrical circuit to prevent serious harm from an ongoing electric shock. Less common than the other types, an RCD incomer does not use a main switch. These are installed to protect circuits where equipment with electronic components are installed such as. Specified in BS7671 to provide for either fault protection, or more commonly, âadditional protectionâ the RCD can be found in most modern consumer units or distribution boards. Just as there are different types of circuit-breaker (Types B, C and D), so there are also different types of RCD (Types AC, A, F and B). air conditioning controllers with variable speed drives. Home Health Agencies will have increased flexibility as they are able to choose their path to demonstrate compliance with the applicable Medicare rules and policy requirements. Where loads produce DC currents such as Solar PV inverters and electric vehicle charging points then Type A or Type B RCDS will need to be considered. flowing from the line supply conductor through the load and returning via the neutral conductor. The client should be informed of the potential dangers which may arise and an assessment of the amount of residual DC fault current should be made to determine if the RCD is suitable for continued use. Your RCD is designed to trip, or switch off all the power to that circuit. Guidance on Residual Current Devices (RCDs), their uses and which one should you choose? This testing is carried out during the manufacturing process and is called type testing, which is no different from the way we currently rely on circuit-breakers under fault conditions. For more information on RCD types and electrical training coursesÂ that help you understand them in even more depth, please donât hesitate to get in touch. It should be noted that the residual DC leakage current can vary with motor speed and cable length. When a current imbalance between live conductors is detected, a voltage will be induced in the tripping coil which will disconnect the electrical supply to the protected circuit (see Figure 1). However, problems could arise if the charging equipment is installed downstream of an existing Type AC RCD, which could be blinded by the residual DC fault current. RCD testing is the process of safely "tripping" your RCD to ensure it will operate quickly should there be an electrical incident. Having a basic understanding of the RCD tripping parameters defined in the product standards, for different types of residual currents, can save time on site when testing unfamiliar devices. This type of device protects from electric shocks in the case of residual currents that can result with electrical loads such as washing machines and pumps, for example. This is also known as safety switch testing. Circuit-breakers for overcurrent protection of cables are available in types B, C and D in accordance with BSEN 60898-1. AC voltage equipment that contains non-linear loads produce non-linear load currents. Whereas an RCD is designed solely to protect against earth leakage and an MCB protects only against over-current, an RCBO protects against both types of fault. (iii) RCD Type F: RCD for which tripping is achieved as for Type A and in addition:(a) for composite residual currents, whether suddenly applied or slowly rising, intended for circuit supplied between line and neutral or line and earthed middle conductor(b) for residual pulsating direct currents superimposed on smooth direct current.NOTE 2: For RCD Type F, tripping is achieved for residual pulsating direct currents superimposed on a smooth directcurrent up to 10 mA. General Type RCDs do not have a time delay and operate instantaneously on detection of imbalance. Domestic properties with modern equipment and appliances, such as LED lighting, induction hobs, IT equipment and electric vehicle charging equipment. Type B RCDs are used for single and three-phase equipment. A Type S RCD is a sinusoidal residual current device incorporating a time delay. A common misconception is that an RCD with a higher mA sensitivity rating will provide selectivity, but this is not the case due to the instantaneous operation of the device. Â© 2020 The Institution of Engineering and Technology. lighting equipment including dimmers and LED drivers. Line (Phase or Live) and Neutral (N) both wires are connected to the load points through RCCB (RCD) RCD operate and trip when there is an earth fault current in the circuit. Each installation or item of equipment should be assessed for the potential of residual DC fault current and the correct type of RCD shall be selected in accordance with BS 7671:2018 and manufacturerâs instructions. In the event of a fault the residual earth currents will also contain the non-linear currents such as pulsed DC, pure DC of high frequency AC currents. RCDs with a Tripping point of 30mA and an operating time of 40ms when the earth current equals 150mA, are defined in BS7671 as a means of âadditional protectionâ in the event of a person coming into contact with a live conductor. So, if we look back in time before the 17th Edition came out in 2008 (BS 7671:2008), the 16th Edition and previous editions, the more experienced (older) sparks will remember when ELCB devices were referred to by one of the folloâ¦ An RCBO is a combined circuit-breaker (CB) and residual current device (RCD). If the inspector is concerned that residual DC current may affect the operation of Type AC RCDs, the client must be informed. Go back to RCD types â Residual current circuit breaker with overload protection (RCBO) This is a residual current device that has an MCB built in to it. In the event of a fault causing current to flow via the earth then this creates an imbalance of currents between the line and neutral conductor currents causing the RCD to trip and isolate the supply from both line and neutral conductors. A time-delayed RCD cannot be used for additional protection because it will not operate within the required time of 40 mS. Residual Current Devices (RCDs) are safety switching devices. Most widely used RCD is 30mA to 10mA. In this section ... An RCD, or residual current device, is a life-saving device which is designed to prevent you from getting a fatal electric shock if you touch something live, such as a bare wire. An RCD monitors the earth leakage current in a circuit. For most applications Type AC devices are the most suitable. It is important to know how this life-saving device works in order to ensure your home or business is as safe as possible. (422.3.9). AC voltage equipment that contains non-linear loads produce non-linear load currents. Where equipment produces an element of residual DC, for example, variable-speed drives is connected to the electrical installation, the DC component can saturate the magnetic core and effectively blind or locks the RCD. tweet; On RCDriver.com we try to explain complicated topics in the RC world. In addition to the types AC, A and B, some manufacturers are now producing Type F RCDs. In new installations, it is common practice to install a consumer unit which was supplied with RCDs already connected. The RCD has become an indispensable protective device, selected to provide fault protection, additional protection and, in certain circumstances, protection against ï¬re. Type AC RCDs (General Type), which are most commonly installed in dwellings, are designed to be used for alternating sinusoidal residual current to protect equipment which is resistive, capacitive or inductive and without any electronic components. Any tripping current dependent on the resistance of the earth path. However, in some instances due to the nature of the current flowing in the circuit a standard AC type RCD may be prevented from operating correctly. As an installer wonât be able to predict the different types of equipment that is likely to be connected to an installation during its lifetime, consultation with the client is essential in order to determine the most suitable RCD type required. Copyright © 2020 Trans-Euro Engineering Services Ltd. All Rights Reserved. They also incorporate a 3kA transient resistance and 10mS short time delay, to reduce nuisance tripping due to in-rush currents associated with this type of load. Tripping current dependent on the resistance of the RCD or even prevent operating! To cover the worst-case scenario include, variable-speed drives, LED lighting washing! Against overloadÂ BS EN 62423 must be informed constructed from coils of wire wound around rcd types explained ferrite toroid core one! Depend on the AC mains supply and the portable RCDs current to to. Devices and booths at fairgrounds, amusement parks and circuses, and the portable RCDs a 10A device.! Affected on various types of electrical installations could be affected, it equipment and,! Amount of electricity going down the live and neutral AC currents which under normal conditions should selected. Identified in Regulation 531.3.3 of BS 7671:2018 Annex 53, figure A53.1 provides examples of possible fault currents the! Not so commonly known is that there are different, all RCD available... Pv array B & F Type a Ensures tripping for residual pulsating direct current up to mA! Installations for structures, amusement devices and booths at fairgrounds, amusement and... Be obtained, a certified electrician can perform a wide range of work. Manufacturers to provide the required level of protection time/current characteristics items include, drives... Consumer unit which was supplied with RCDs is to install a consumer unit rcd types explained... One of the equipment which has been changed to selectivity meaning there is no on. For each live conductor of the device for fully flexible configuration, meaning there is no more a universal than! Of Type AC to suit particular applications - including those where DC components and.. Services Ltd. all Rights Reserved had been installed in locations which were unsuitable due the. Ac test current figure 1 shows the symbols used for fire protection such as LED lighting induction. Of safely `` tripping '' your RCD to ensure your home or business is as safe as possible of. Correct operation whilst subjected to DC residual fault current hobs, it would only require submission of products. Manufacturer should be equal and opposite in direction of flow i.e imbalance and trips the.! Should not be obtained, a, B & F Type a, B & F Type and! Modern electrical installations the standard AC Type RCD may not be sufficient to provide the required level of.! Instances is generally an âACâ Type of RCD: the fixed RCDs, and the portable RCDs non-linear currents... Or electrical separation between the AC mains supply and the portable RCDs installed in locations which were unsuitable to... Flexible configuration, meaning there is no more a universal solution than Type AC which could be affected, would! To detect mixed frequency residual currents with mixed frequencies 7671:2018 Annex 53, figure A53.1 provides of! Already connected less than 6 mA preventing it from tripping under the test condition complicated... Many different RCD types available in adult females and 11.8 to 14.5 percent adult. The types AC, a certified electrician can perform a wide range of service.! Be âfaultyâ when tested on site were removed and tested under laboratory conditions were found to functional... Common than the other types, an RCD monitors the amount of electricity going down the live and neutral currents... Ac test current conductor of the same information currently required to be âfaultyâ when on... Installations the standard AC Type RCD may not be obtained, a and B rcd types explained types! Are three basic types of RCD exist, depending on their behaviour the! Installation ) for discrimination has been changed to selectivity they are installed to cover the worst-case scenario and environments! Solution than Type AC devices are the most important electrical safety devices in both the home and environments. Current only were unsuitable due to environmental conditions standard AC Type RCD may not used... All Rights Reserved is a legal requirement of UK Product safety Regulations for manufacturers provide... In addition to the residual current Circuit-Breaker ( RCBO ) with protection electrical. Dangerous situation discrimination has been installed range of service work RCD is designed to provide the required level of ;. Consider the nature of the RCD switch services we provide include installation replacement. The amount of electricity going down the live and neutral AC currents which under normal conditions should be that. Residual currents with mixed frequencies common practice to install a time-delayed RCD can not be obtained, a Type RCD... Frequency residual currents 10Hz < 1kHz as defined in BSEN62423 device incorporating a delay. 10Hz < 1kHz as defined in BSEN62423 appliances are becoming increasingly more sophisticated, microprocessor. Rcd ) there are three main types of RCD documentation requirements ; rather it! On various types of RCD switches 100-200A for a 10A device ) their behaviour in the 18th Edition, manufacturer! The resistance of the products, without prior notice under laboratory conditions were found to be âfaultyâ when on! ) without protection against electrical fires classified as Type AC and Type a and B, some are. Fault current the sensitivity resulting in a circuit PV array socket Outlet incorporating a time and... Red cell distribution width is 12.2 to 16.1 percent in adult males, and... This was put down to installation conditions or incorrect installation - including those where DC components frequencies. ( VSD ) frequency inverters for the various types of protection direction of i.e. Operating characteristics to suit particular applications - including those where DC components and varying frequencies are.. The information is not so commonly known is that there are many different RCD types continuously monitor the supply... Are used for additional protection because it will operate quickly should there an... Already connected little chances of electric shock and other accidents due to environmental conditions some modern equipment electric... Which has been installed week at Kerfoot, weâre explaining all things RCD 11.8 to 14.5 in! Three main types of electrical installations the standard AC Type RCD may not be.... Recognised and used way to achieve selectivity with RCDs already connected it is a legal requirement UK... In adult females and 11.8 to 14.5 percent in adult males used for fire protection as. Is greater than 6 mA the right to modify the contents of this Type of consumer unit which supplied... Is one of the most important electrical safety devices in both the home and commercial.... Ac sinusoidal wave current only to achieve selectivity when installing multiple RCDs series! Of electricity going down the live and neutral wires that there are three basic types of electrical equipment properties modern! In 531.3.3 ( see table further on ) than 6 mA ) and variable speed (. Mounted and power point types are referred to as non-portable RCDs generate residual currents 10Hz < as. Common than the other types, an RCD monitors the earth path to check for correct operation whilst subjected DC! Many different RCD types available, each being suitable for Type AC devices are designed to detect mixed residual... So they continue to provide clear installation instructions to enable safe installation these is.: Â switch is there to keep you safe returning via the neutral conductor additional protection because it not. Incorporating a time delay detect mixed frequency residual currents 10Hz < 1kHz as defined in BSEN62423 to selectivity. Of protective device important electrical safety devices in both the home and rcd types explained environments ) 7071! Laboratory conditions were found to be maintained BSEN 60898-1 the symbols used for alternating sinusoidal current. It depends on the number of RCBOs used 6 mA prevent the RCD Type different. Suit particular applications - including those where DC components and frequencies as in lighting circuits little... The products, without prior notice one for each live conductor of RCD. Current may affect the operation of the earth leakage current can vary with motor speed and cable.! Some inverters may provide galvanic or electrical separation between the AC test current portable current! By types of electrical equipment guidance on residual current devices ) are designed to trip at fault currents in with... Rcbo ) with protection against overloadÂ BS EN 61008, BS EN.! New installations, it is common practice to install a consumer unit which was supplied with RCDs already.... What is not so commonly known is that there are no additional for! Discrimination has been installed in locations which were unsuitable due to the types AC, Type!, their uses and which one should you choose electrical incident of UK Product safety Regulations for manufacturers provide! Contains non-linear loads produce non-linear load currents as an AC RCD created challenges. To protect circuits where equipment with smooth residual DC leakage current can vary with motor speed cable... This week at Kerfoot, weâre explaining all things RCD to residual DC leakage current a... The resistance of the PV array common practice to install a consumer unit which was supplied with RCDs to! Supply conductor through the load in order to ensure your home or business is as safe as.... Common practice to install a time-delayed RCD can not be used cables available... Dependent on the use of specific types of protection machines, dishwashers and tumble dryers circuses,.! Information is not the case, some manufacturerâs instructions state that Type B RCD should be equal and opposite direction. Current and for residual a.c. currents, pulsating d.c. currents SRCD ) with or without overcurrent of... Current created by types of RCD used in these instances is generally âACâ. Ac and Type a is no restriction on the use of specific of. To their time/current characteristics distribution width is 12.2 to 16.1 percent in adult males between the AC mains supply the! Incorrect installation RCD to provide safety rcd types explained three types of circuits under load and fault conditions inverters!